How to Repair a Burst Pipe
Fix it and prevent it from freezing again with these instructions.
E-mail This Page to Your Friendsx
A link to %this page% was e-mailed
You don't need advanced plumbing skills to fix a burst pipe -- just some soldering equipment. And by adding a stop and waste valve, you'll be going a long way toward ensuring that the pipe doesn't freeze again. Here's what to do:
Materials and Tools:
mini copper-pipe cutter
torch kit (torch and striker)
good ½-inch copper pipe
stop and waste valve
½-inch copper fittings
1. Determine a location for the valve on a water line in or near a heated area.
2. Shut off the main valve where water comes into your home. Open the lowest fixture in your house to drain any water out.
3. Use a pipe cutter to remove the desired section of pipe. Rotate the pipe cutter around the pipe, gradually tightening it until it cuts through. Clean any burrs off the end of the cut pipe with steel wool. Place a bucket under the cut area to catch any water remaining in the line.
4. Temporarily remove the petcock (small screw) from the valve. Be sure to install the valve in the right direction. An arrow points in the direction of the water flow.
5. Cut a section of copper pipe to the appropriate length. Allow a little extra length for a good fit. Be sure the new pipe is of the same diameter as the existing water line (usually ½-inch).
6. Use steel wool to clean both the pipe end and inside the stop-and-waste valve.
7. Spread soldering flux on the outside of the pipe end and inside the valve fitting.
8. Slide the valve fitting onto the end of the pipe.
9. Wearing safety goggles, use a propane torch to heat the fitting and the pipe where they connect. For best results, hold the edge of the blue flame right against the pipe.
10. Push about 2 inches of solder into the joint where the valve connects to the pipe. The heat will melt the solder and allow it to seep into the connection. Solder completely around the pipe-valve connection. Practice the soldering technique on scrap pieces of pipe and copper fittings before trying it on the valve.
11. Use the same soldering techniques to install the new assembly to the water line. Depending on the installation, it may be necessary to use some inexpensive copper fittings to connect new sections of pipe to the existing water line. These copper fittings are widely available in different configurations and diameters.
12. Replace the petcock, and open the main water line to check for leaks. Before temperatures dip below freezing, shut off the valve and open any spigots that are downstream of the valve. Then remove the petcock screw to drain the pipe. If any sections of pipe upstream of the new valve are in an unheated area, cover them with foam pipe insulation.